Water-resistant box for protection and branching for public lighting, with a polycarbonate casing.
Protection of the lighting point is by means of cylindrical 10×38 type T-0 fuses.
There are two terminals for connection or output of lighting point, accepting cable max. 6 mm2 each.
Inside there are dtwo DIN rails. In the upper part, there is a fuse holder base and on the lower, a SERTEM type terminal strip with 4 input/output terminals accepting max. 2 cables of 16mm2, offering the possibility of sharing the electrical load between the different phases by means of the Faston connectors on the cables.
There is an option to install a DIN SERTSEM type terminal strip with 3 terminals accepting max. 2x16mm2 to connect the earth and/or the double level/ flow.
Degree of protection IP44, IK08, Double Insulation, Class II, CE marking.
Keep pressed to zoom